This question was originally posted on DCIM Support by Balaraman Jagadeesan on 2016-08-27
I would like to share the Connection diagram of the Buzzer/Sound Alarm for those who want to receive Sound Alarm when there is violation of Netbotz Sensors Thresholds. I hope this helps.
The Relay NO/NC Outputs as an Action to threshold violations can be configured on Netbotz 200 & Advance View for Netbotz 450/570.
I hope this helps.
This comment was originally posted on DCIM Support by Vineet K. Sarin on 2017-06-09
Very nice Bala...quite helpful.
This comment was originally posted on DCIM Support by Garry Priestland on 2017-06-09
I have also done it a similar way before, but be aware that the supply from the 12V and 24V connections shown are very weak, capable of only 75mA total output. So if you choose a sounder that demands more than 75mA current, it might not work too well.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!