On internet I found 3-phase capacity planning worksheet and per calculation on this sheet those phase values are much higher than 16A, when banks are loaded. Also I was on chat with APC support I they told me that those phase value are just fine, but I am not convinced yet 🙂. Additionally we had overload warnings during relatively low load.
This is only 4.7kW on device that can handle 17kW! What will happened when we push load up to 6-7A per bank, on all 6 banks?
Can somebody calculate load per phase if load for every bank is 6A?
Can anyone give more explanation? Do you folks think that this is OK and I do not need to be worried?