This question was originally posted on DCIM Support by ADEKUNLE AGBOKE on 2018-08-23
I have an "APC Modular Power Distribution Unit, 266kVA, 400A, 480V:415V Auto-transformer, 72 Pole" which we monitor via struxtureware.
Solved! Go to Solution.
This answer was originally posted on DCIM Support by Steven Marchetti on 2018-08-23
1: If DCE loses communications with another APC device, the device itself can be accessed (assuming it is on-line) and you can view the data and event logs for information. This data however can not be imported to DCE. DCE will only put sensor data in the database for those sensors it was able to poll using the defined protocol for that device (ie. SNMP/Modbus).
2: Since you can not import data into DCE from data logs, when DCE loses SNMP/Modbus connection to a device, there is no way to avoid a loss of data or a gap in the graph created from that data.
This answer was originally posted on DCIM Support by ADEKUNLE AGBOKE on 2018-08-24
Thanks very much for the information
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!