I have new model Netbotz 750 series and would like to integrate with fire suppression FM200, and the FM200 panel have NO/NC module which is able to connect.
However, I am not sure which port of Netbotz 750 able to connect to panel FM200.
You will need to connect the FM200 NO/NC Module to Netbotz 750 using the NBES0304 Netbotz Dry contact sensor. (https://www.se.com/ww/en/product/NBES0304/netbotz-dry-contact-cable---15-ft./) NBES0304 is connected to Netbotz 750's Universal sensor ports.
Please take note that the NO/NC module from the FM200 is "voltage-free" connection with NBES0304.
The NetBotz 75x offers an active monitoring solution designed to protect against environmental threats and unauthorized access risks that can cause downtime to IT infrastructure, in both Edge Compute and Data Center environments.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!