This question was originally posted on DCIM Support by petru bunea on 2018-12-18
Would it be possible that by using the NBES0304 dry contact cable in the Netbotz 450/550/570 along with several Ap9619 SMART UPS NMC I could get an SMS when powere is out or when the UPS has a fault ?
I've read that the Ap9619 has a configurable relay that is able to close or open on event basis. This led me to think that I could hook up a dry contact cable from Netbotz appliances to a NMC card relay and get useful information via SMS (and via e-mail of course) in the event of a power outage or something similar.
This comment was originally posted on DCIM Support by Steven Brown on 2018-12-18
That would likely work but the recommended solution for this requirement would be to use a NetBotz 570 with the 5-node monitoring license (NBWN0006) to discover the NMC, and then configure an alert based on its status.
This comment was originally posted on DCIM Support by spezialist on 2018-12-18
Dear petru bunea,
I think if a ethernet network is available for your UPS, then it’s better to just use its NMC without even connecting and buying additional licenses for the NetBotz-4.x appliance.
Indeed, in the above mentioned NMC there is a complete set for event notification, including by e-mail. And if you want to be notify via SMS, then you can use public email to SMS gateways of mobile operators in your country.
This comment was originally posted on DCIM Support by spezialist on 2019-01-05
Dear petru bunea,
Please tell us if you could solve your question or not?
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!