This question was originally posted on DCIM Support by E W on 2019-02-27
Does anyone know how to create an alert for when a door sensor is open that it triggers the relay output?
From my research it appears this should be possible from the Netbotz Advanced view software but i cant get it to add the Netbotz 250 it just keeps kicking me to the login page.
This answer was originally posted on DCIM Support by Cory McDonald on 2019-02-27
The NetBotz 250 does not utilize the advanced view software. I do not believe that the rack access door switch sensors can be utilized to control anything within the NetBotz Appliance that is not directly related to rack access.
In order to have a door sensor trigger a relay output, the door sensor would need to be connected to one of the 6 universal sensor ports or a sensor port on a sensor POD 150.
Within the 250's web interface, navigate to: Configuration > Device > Outputs > Relay Output. Here can you configure "Input State Sensors" for "Abnormal State".
This comment was originally posted on DCIM Support by spezialist on 2019-04-01
Dear E W,
Tell us, please, did you solve your question or not?
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!