I am trying to integrate Netbotz into my Scada system using modbus TCP. I was able to find the register address here:
I can access all of the main modules registers using the register number on the page. However, when I try to access the expansion modules, I cannot access any of it.
I found an old thread regarding Netbotz 150 modbus from 2017 https://community.exchange.se.com/t5/EcoStruxure-IT-forum/Sensor-Pod-150-ModBus/m-p/216776
Can anyone assist and verify if you can access the expansion modules with the address noted in the pdf document above.
I thought this had been added as well but I'm seeing no values coming from the extended modules while I do have modbus out with the rest of the unit. I'm running the most up to date firmware with another due out soon but I don't know of anything modbus related in that update:
Hi @qle303 ,
Sorry I neglected to get back to you on this. It does seem to be an issue and although some registers are working, others are not and those that do work don't seem to align with the register map. I've added this issue to the tracking system so that engineering can address it. Sorry I can't provide an ETA.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!