This question was originally posted on DCIM Support by shemilusman on 2018-07-19
Please requesting to provide the DDF's for Uniflair cooling units TDTV1622A & UCA0481, both projects DCE configuration is not signed off because cooling units sensor values are blank.
This answer was originally posted on DCIM Support by spezialist on 2018-07-20
Register (for free) on the web-resource http://webcard-it.schneider-electric.com/enterPanel.asp. Then download the file CRAC_DDF.zip for ROOM AIR CONDITIONING and TELECOM.
Unzip the zip-file and read two files readme_association_DDFs.txt (depending on the connection type of your cooling units to DCE-server: SNMP or TCP/IP Modbus).
For Unitel UCA telecom ceiling air conditioners, as explained in the above text files, it is necessary to use:
MODBUS_TCPIP: uniflair_sp_uniflair_wm_uniflair_mb_telnew_TCPIP_Modbus_CCU.xml => Telecom units (W*) or (X*) or (U*) or (ADD*) series
SNMP: uniflair_sp_uniflair_wm_uniflair_mb_telnew_SNMP_CCU.xml => Telecom units (W*) or (X*) or (U*) or (ADD*) series
SNMP for Telecom multiple units case: uniflair_sp_uniflair_wm_uniflair_mb_telnew_SNMP_CCU_multiple.xml => read CW_Sensors_pCOWeb_guide.txt file!
For Uniflair LE (Leonardo) TDTV room air conditioners, as explained in the above text files, it is necessary to use:
MODBUS_TCPIP: uniflair_am_le_DX_ug40_pCO1_TCPIP_Modbus.xml => S*(a/W)* / T*(A/D/W/T)* series Direct Expansion
SNMP: uniflair_am_le_ug40_DX_SNMP_CCU.xml => s*(A/W)* / T*(A/D/W/T)* series Direct Expansion
SNMP for UG40 DX in case of CW and DX files distinction or Telecom presence: uniflair_am_le_ug40_DX_SNMP_CCU_multiple.xml => read DX_Sensors_pCOWeb_guide.txt file!
If this does not work for you, then in the above mentioned text files there is an e-mail, where you can and should apply for help.
I hope this is what you need.
This comment was originally posted on DCIM Support by shemilusman on 2018-08-20
Dear @spezialist, system and radio engineer,
Please note that in the mentioned web-resource http://webcard-it.schneider-electric.com/enterPanel.asp , there is no option to download CRAC_DDF
Only available resource is CRAC_Modbus, CRAC_MIB etc. and for CRAC_DDF it will divert to http://sxwhelpcenter.ecostruxureit.com/devices
So please develop the DDF's for Uniflair cooling units TDTV1622A & UCA0481
Thanks & Regards
This comment was originally posted on DCIM Support by spezialist on 2018-08-20
Yes, that's right, you were late with the answer for exactly one month (my reply of Jul 20, 2018 😀. Therefore, a month later on the above-mentioned web-resource there are some changes:
Ok, here is the CRAC_DDF.zip, about which I wrote above. Try the above DDF-files and tell us, please, the result.
If you have any more questions, please ask.
This comment was originally posted on DCIM Support by spezialist on 2018-07-29
Tell us, please, did you solve your question or not?
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!