This question was originally posted on DCIM Support by DCIM Support on 2014-06-11
In InfraStruXure Central (ISXC) 5.0.x, mass configuration of APC devices is not an available option.
In ISXC 5.1 and StruxureWare Data Center Expert there is a mass configuration option for APC devices. There are options where you can pull the configuration from one device and push that configuration to one or more devices. This option will not, by default, pull the user name and password from the initial device?
This answer was originally posted on DCIM Support by DCIM Support on 2014-06-11
There is an option however to edit the configuration after it is pulled from the initial device and before it is pushed to the target devices. The user name and password of the device can be changed and pushed to the target device(s) to mass configure the user name and password. After ISX Central / DCE pushes the config, it will try to pull it from the device again to verify what it sent against what the device is providing in the configuration file. Since we can not pull this value to verify it, ISX Central / DCE will show an "Incomplete Configuration" error message. The value should be pushed however and logging in with the new password will verify this.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!