This question was originally posted on DCIM Support by Martin Gaciarz on 2019-11-04
We had 83 out of 84 devices in a group set to be in Maintenance Mode for the past few days. This morning, we got alerts on a bunch of these devices. I double-checked and they still show up as being in Maintenance Mode in the DCE console... what went wrong here?
This answer was originally posted on DCIM Support by Jeff Shaw on 2019-11-05
Check the web interface of the devices for email configuration. If email notifications are configured on the device itself, they will still send emails. Maintenance mode only disables notifications sent by DCE.
This answer was originally posted on DCIM Support by Andres Alfredo Gonzales De La Cotera Herrera on 2019-11-05
Try to check`s recipents of all decivices in each interface web. Becauses maybe the problem is there. And try to do a test When you active any parameters in the DCE.
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!