This question was originally posted on DCIM Support by JAVIER APONTE on 2019-05-23
I need to install 12 AP9520TH, through 01 NBRK0250
Could you please tell me if that is feasible?
If so, what accessories are required for this?
Solved! Go to Solution.
This answer was originally posted on DCIM Support by Justine Chester on 2019-05-23
The maximum number of AP9520TH that can be added to the Netbotz 250 is eight (8).
These sensors are cascaded using Cat5 cables through the A-link ports with terminators on both ends of the line (A-link IN of the Netbotz 250 and A-link out of the 8th AP9520TH) to avoid communication loss.
To know more about this, please refer to page 10 of the Netbotz Rack Monitor 250 Installation and Configuration Guide from the Documentation section of this website.
I hope this helps.
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!