This question was originally posted on DCIM Support by Mian Aqeel on 2018-04-16
How to change email notification units from F to degree oC centigrade of Rack monitor 570 sensors email notification,
This answer was originally posted on DCIM Support by Christopherus Laurentius on 2018-04-16
When you create the email alert action, select locale for the email.
In the Basic tab, click Add..., enter E-mail Addresses to which the alert notification is to be sent, select the language and territory using the Locales drop-down list, then click OK.
This answer was originally posted on DCIM Support by Mian Aqeel on 2018-04-26
Hi Christopherus Laurentius,
Hope you are fine and doing well. Here is problem still facing
Netbotz Rack monitor’s Sensors notification Alert by email are not configuring in Centigrade. (as already setup Netbotz from DCE alarm actions : Manage Alarm Action -> Edit -> Locale (changed to English US & English Metric) Sensor graph has changed to Centigrade but still sensor value is showing in Fahrenheit) .
This comment was originally posted on DCIM Support by Christopherus Laurentius on 2018-04-26
Same as above, but do it under netbotz' alert action, not DCE.
This comment was originally posted on DCIM Support by spezialist on 2018-04-28
Dear Mian Aqeel,
Have you been able to solve your problem, or do you have any more questions about it?
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!