This question was originally posted on DCIM Support by Per Bergman on 2019-03-20
DCE send the Netbotz critical alarm of Expansion module log-term decrasing temperatur rate when we open rack doors in hot isle. I cant find any way to adjust any threshold value to avoid these alarms.
Solved! Go to Solution.
This answer was originally posted on DCIM Support by Steven Marchetti on 2019-03-21
Assuming a NetBotz 450 or 550/570, you would launch the Advanced View software and connect to the appropriate appliance. Select the pod and then right click the offending sensor on the left panel and chose "Configure Sensor":
You'll see the associated thresholds. Select the correct one and hit edit:
You can then configure the threshold's settings:
If you have the NetBotz 250, log into it's web interface and you should see temperature and humidity sensors, click on "More" on the right. :
Find the appropriate sensor/module and click the link. In this case, Sensor NB:4:
You can then choose rate of change settings (which would seem to be what you're looking for) or thresholds:
This comment was originally posted on DCIM Support by Per Bergman on 2019-03-26
Thanks for a good answer!
I have som problem loggin in to the Netbotz unit. It says
Should i try to restart it? //Per
This comment was originally posted on DCIM Support by Steven Marchetti on 2019-03-26
Again, you've not told us what device you have. I'll assume it's a NetBotz 250 because most others do not have limits to the number of users that can log in. A physical reboot should help. You can also try logging in using ssh (if enabled) and back out. You can try another browser, and another computer as well.
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!