DCE has been updated to the latest version 7.8.1 and some devices with tcp modbus and snmp protocol; the option to start on device within expert we do not have access to your page. Web.
- from DCE I can monitor (I see all the sensors of the equipment)
- It is worth mentioning that in the local network I can access the page. Web
Does anyone know anything about this problem?
DCE launch to device will in many cases not work on a Modbus device as the IP is usually that of a gateway and not necessarily to the device itself.
Another thing to think about is if this is an APC device or not .If it is not, you will not be able to have DCE auto-login to a device. Even with an APC device, you have to manually configure the device launch settings as the user name and password and http vs https are not automatically configured.
Another potential issue is if the device is on the DCE private LAN, you'd need to have everything (device launch settings, http vs https, TLS versions, etc) all configured properly. Additionally, DCE will only launch to devices within the DHCP scope of the private LAN and the private proxy is only enabled when the DHCP configuration is enabled. Additionally, if you have HTTP disabled on the DCE server and the private LAN device is trying to launch via HTTP, the connection can not be made because it is disabled on the server.
I'd try to help more but I think this would require a lot more specifics on your part and you might get a quicker response if you contact tech support directly by phone.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!