This question was originally posted on DCIM Support by Krista Flynn on 2019-01-03
Someone suggested that I needed to update the DCE to 7.6, which would give me the most current DDFs. I have updated the DCE to 7.6 and also updated the PDU firmware and I still don't see the kVA sensor.
This answer was originally posted on DCIM Support by Steven Marchetti on 2019-01-03
I checked an AP7911B via SNMP using the following OID:
The return was a -1. This indicates that voltage is not supported by this device. Without voltage, you can not get wattage. The DDF can not calculate it outside of the device as it will do in some instances. The device does support current, but not wattage or voltage.
rPDU2PhaseStatusPower also reports a -1
It simply appears that this device does not support a watt or KW sensor.
This comment was originally posted on DCIM Support by spezialist on 2019-02-09
Dear Krista Flynn,
Tell us, please, did you solve your question or not?
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!