This question was originally posted on DCIM Support by Vincenzo Fantino on 2018-03-13
I have configured a DCE (7.5.0) as an External System Configuration to DCO (8.2.2), but the Data in DCO device window doesn't match with the data on the device:
This answer was originally posted on DCIM Support by Christopherus Laurentius on 2018-03-14
DCO will take peak power over the period based in settings for "calculate power data based on days' per picture below.
By default, it will keep last 30 days data.
The rack PDU NMC showed peak power of 10.11 kw back in 09/16/2015, which is more than 30 days.
For more information:
This comment was originally posted on DCIM Support by Vincenzo Fantino on 2018-03-14
I was referring at the total KW, as you can see from the pic on the device is 7.78KW and in DCO is o KW
This comment was originally posted on DCIM Support by Christopherus Laurentius on 2018-03-15
Now that you mentioned, the average power is shown as zero, and the average individual phase power has no data in DCO.
Jef Faridi, any idea?
I've highlighted Enzo's original screenshots on the average power:
This comment was originally posted on DCIM Support by Vincenzo Fantino on 2018-03-20
I think I have found the solution, I applied the patch at:
and now I am getting the right value
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!