This question was originally posted on DCIM Support by juice on 2017-05-11
Good day all
I am struggling to find an easy way to run a report - in DCE &/or DCO that can do the following for me;
- total power in current (amps) for cabinets - Row A - to Row I,
- total current for individual cabinet
- total current per feed (Single phase A feed and B feed, Three phase A feed and B feed)
Currently, I am simply extracting all the current for each PDU, for each row and for each power feed. This is extremely exhausting. Is there a simpler way of creating this report?
Thank you in advance for taking the time to respond. Much appreciated.
This answer was originally posted on DCIM Support by Steven Marchetti on 2017-05-11
If you're saying that you have for example 10 amps per rack and you want to see A-I added together, you'll want to use virtual sensors in DCE. A virtual sensor can sum or average numerous values.
If you have multiple PDUs or other values per rack, you can create rack total sensors, row total sensors, room total sensors, etc. Setting this up may be time consuming but you have to only do this once and running future reports is as simple as running the reports on the virtual sensors.
This answer was originally posted on DCIM Support by Vineet K. Sarin on 2017-05-11
Hi Juice ,
We developed a Framework with a third party to work with DCE and DCO reporting system which can generate pretty much any type of report you want to generate from these systems using SOAP/REST/WEBSERVICES etc.
I have attached sample of few reports that we have done for couple of clients. Mail me offline and I may be able to help you with the same.
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!