This question was originally posted on DCIM Support by Kaloyan Georgiev on 2016-08-08
I have installed PME 8.1 and DCE 7.3.1 with Modbus TCP module.
When I try to read some data in PME from DCE, I get an "Invalid data address" modbus error. It is not a timeout, so the communication is working.
Can you help me connecting the two softwares together?`
The information about the error is in the attached pictures.
This answer was originally posted on DCIM Support by Law TJ on 2016-08-08
Hi, try to read with 331020 instead. Thanks
This comment was originally posted on DCIM Support by Law TJ on 2016-08-08
Modbus TCP output only able to start from register 31000 as the option when you generate the register list "Please choose a register value between 31000 and 39999" So you may need to read as Input register, @31000, and in Modbus address, the register address will be 331000
This comment was originally posted on DCIM Support by Stine Hansen on 2016-08-11
Hi Kaloyan Georgiev, did you try the suggestions above? Best, Stine
This comment was originally posted on DCIM Support by Kaloyan Georgiev on 2016-08-15
Hello, I tried and I have a success. The problem was that instead of address 31020 i should use 331021. Now everything is OK. Thank you for the support! Regards, Kaloyan
This comment was originally posted on DCIM Support by Stine Hansen on 2016-08-15
That's great news, Kaloyan Georgiev! Thanks for sharing. Regards, Stine
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!