We are getting incorrect readings from inRow ACRD301 (rd3xx -v6.6.4k, aos - 6.6.4). The temperature values in Celcuis are read in values of Fahrenheit (the voltage values are incorrect as well) as attached. We also found that the status of Inrows are all in Standby (but in fact 2 units are running).
We are using DDF - apc_acrd2g ver 14 but no luck.
Anyone encounter this before?
Can you do an SNMP walk of the cooler?
It is possible that this is not a DCE issue but that the cooler is presenting the wrong information to the DCE.
Thanks for the suggestion. I will upload the walk files once I gather them.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!