This question was originally posted on DCIM Support by sheep on 2020-01-05
I want to update the Date & Time using SNMP Device Configuration,
However, I have a problem when I tried to configure few PDUs:
Under the column - Last Retrieved appears "Not Retrieved (in red color)"
Moreover, I have to do not mark in the hostname checkbox in order to
continue to Configure Device Settings.
What can I do to fix this?
This answer was originally posted on DCIM Support by Mate Fekete on 2020-01-06
I'm just another user who had similar problem in the past. It was related to blocked firewall ports/protocols especially where DCE wants to send configuration to the device (21 or 22).
See more details here:
This comment was originally posted on DCIM Support by sheep on 2020-01-07
Tank you for the help, but the problem is not blocked firewall and
I noticed that the problem appears on a specific model AP8853: 32A-1PH.
Do you have this model?
This comment was originally posted on DCIM Support by spezialist on 2020-01-07
Can you show a screenshot of the firmware version from the web-GUI of your problematic AP8853 rPDUs?
This comment was originally posted on DCIM Support by sheep on 2020-01-08
The firmware version:
Rack PDU: 6.5.6
APC OS(AOS): 6.5.6
Boot Monitor: 6.5.6
This comment was originally posted on DCIM Support by spezialist on 2020-01-09
Maybe you should try updating one or two of the above rPDUs to the latest version v.6.8.2 and see the result?
Also, what is your version of DCE software?
This comment was originally posted on DCIM Support by sheep on 2020-01-09
The version of DCE software: 188.8.131.52
I will try update to v.6.8.2 can you please send my a link for download?
But I have a lot of other PDUs with this version 6.5.6 that work great without any problem.
Important notice: the problem that I have is with a specific
model AP8853: 32A-1PH.
Maybe the problem is with this controller version?
This comment was originally posted on DCIM Support by spezialist on 2020-01-10
Unfortunately, I could not find the web-links for the download ☹️. But you can download the latest DCE device firmware catalog, import it into DCE software, and from there update your problematic rPDUs.
I also have many rPDUs of AP8853 and AP8881, all with the latest firmware v.6.8.2. And I did not observe any problems on them.
Hope this helps you.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!