This question was originally posted on DCIM Support by Brendan Mc Cormack on 2019-05-09
I have a Circutor CVM-Mini power analyser setup on DCE but it's showing apparent power in watts only. I need to view it in kW.
The DDF I'm using is one of two Circutor DDF's available to download "Circutor CVM-NRG96-ITF".
The second DDF is "Circutor CVMK" and doesn't work with my CVM-Mini at all.
Can the "Circutor CVM-NRG96-ITF" DDF be altered to give kW readings?
The modbus memory map for the CVM-Mini is on page 23 of the PDF below
This answer was originally posted on DCIM Support by Nicholas St Pierre on 2019-05-22
Attached is a DDF with updated sensors that report in kW. I left the original sensors in watts in case you are currently monitoring this device in DCO as well. For proper DCO association power must be reported in watts, not kW. Let me know if you have any issues.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!