This question was originally posted on DCIM Support by Javier Zurera on 2018-01-12
we have an issue with the capacity overview in a deployment over DCO 8.2.
We have different locations, and in the global view for Scotland we see this capacity overview:
But inside Scotland we only have one floor plan for Glasgow with this capacity:
So both Capacity Overviews should be the same, shouldn't they?
Then inside Glasgow, we have 4 rooms:
Main Room with two small UPSs A-B that feed two in-row cooling machines for a high density area. Each UPS is 40 kW, total in this room: 80 kW
Also in this Main Room we have two rectifiers, A-B, with 2.4 kW each one. Total 5 kW
Room UPS-A with a 540 kW UPS
Room UPS-B with a 540 kW UPS
Another room only with racks.
So, the total capacity of Scotland is 1.165 kW (80+5+540+540).
But we have defined 2N redundancy in all the racks, so we expected to see the half of the total capacity, 582,5 kW for this site.
Where are the errors?
Thanks in advance.
This answer was originally posted on DCIM Support by Christopherus Laurentius on 2018-01-15
Two things, while waiting for the rest to feedback.
This answer was originally posted on DCIM Support by Calum McCulloch on 2018-01-15
I had added 3 new cabinets which caused the 4000kW + increase in reported power, I don't know how it was so much, but I deleted them and both figures are now the same.
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!