This question was originally posted on DCIM Support by Ali on 2019-05-08
Can I use beacon if any alarm occurred on the DCE from different devices.
kindly see the below scenario can I use Beacon for rack PDU alarm.
This answer was originally posted on DCIM Support by Steven Marchetti on 2019-05-09
The beacon does not work with DCE. The NetBotz appliance can alert for anything it is monitoring but it can not be automatically configured to alert because of something DCE is monitoring.
A NetBotz appliance can monitor up to 5 devices itself using SNMP but there is much more manual configuration involved and DCE can be triggered based on a device alert where a NetBotz will always wait for the next poll and will not alert unless you’ve configured the thresholds.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!