This question was originally posted on DCIM Support by Paul Baker on 2016-08-02
Ive just entered a load of servers into a rack in DCO.
The racks physical power limit is 24.54kW (
estimated load is 9.55kW
Potential Failover load is 9.32kW
Im at a loss to understand what this error means with these figures ?
This answer was originally posted on DCIM Support by Gert Lehmann on 2016-08-02
The mentioned recommendation looks a the breaker limit for each power phase on each rack PDU, and will show up if the estimated load + failover load on that particular breaker exceeds the limit.
E.g. if you have a rack with 1 three phase rack PDU and connected all servers to L1, then you have exceed the breaker capacity of L1 at 1/3 of the total rack capacity.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!