This question was originally posted on DCIM Support by Garry Priestland on 2017-06-09
Any reason why the on board clock of an AP9361 PX HID controller should be running very slow?
It seems to lose about 40 mins every 1 hour.
NTP sync works but at this rate of time loss, NTP is not very effective...
This comment was originally posted on DCIM Support by Ditte Drewer Mathiasen on 2017-06-15
Hi Garry Priestland, thanks for posting.
Let's see who can be of assistance here. @community any ideas?
Kind regards Ditte
This answer was originally posted on DCIM Support by Stine Hansen on 2018-02-08
Sorry to leave you hanging.
I hope you found answer.
This comment was originally posted on DCIM Support by Garry Priestland on 2018-02-13
No answer - just appears to be faulty hardware...
This comment was originally posted on DCIM Support by Stine Hansen on 2018-02-14
Oh OK, thanks for letting us know 😀
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!