This question was originally posted on DCIM Support by Enric Climent on 2016-02-22
Our customer has a lot of AP9335TH sensor connected to a Netbotz 570 and sometimes some sensors send a high temperature value, more than 200M degrees. Is this a hardware or software problem? How can we solve it?
This answer was originally posted on DCIM Support by Balaraman Jagadeesan on 2016-02-22
I would suggest you to verify the Botzware version of Netbotz 570. You can upgrade it through Advance View Software under Configuration–>Upgrade option.
The latest Netbotz 570 firmware version is v4.5.1.
Secondly, how many AP9335TH sensors are connected to Netbotz 570? Do you have any Sensors pods connected to the appliance? If so, how many are connected? Is this applying to any specific sensor pod's sensors or all the sensor pods's sensors? If possible, can you please share some screen shots where it shows the wrong values?
This comment was originally posted on DCIM Support by Enric Climent on 2016-02-22
I've already have the v4.5.1 firmware version.
The customer has 14 AP9335TH sensors connected to the Netbotz 570 through Netbotz 150 pods.
Below you can find a screenshot with a wrong value.
This comment was originally posted on DCIM Support by Balaraman Jagadeesan on 2016-02-22
Dear Enric, I see that the screen shot is from DCE version 7.2.6. When the DCE alert shows the reading wrongly in email alert, does the Netbotz appliance's advance view show the correct reading? & What is the reading on DCE under View Device Sensor values for the Netbotz appliance/Sensor Pod? I am trying to understand if this value comes wrongly on DCE email alert or Is the same value shown both on the netbotz appliance and on DCE? or Is it only shown DCE? Secondly, Please make sure that Sensor Pods are connected properly through A-Link Ports by using CAT-5 cable. Please make sure that Cross over cable is not used for connecting Sensor Pod in daisy chain to the appliance A-Link Bus.
This comment was originally posted on DCIM Support by Enric Climent on 2016-03-23
Hi Bala, I've compared the DCE emails with the Netbotz history and the high values are only showed in the DCE email, not in the Netbotz history values. The sensor pods are connected properly. Best regards, Enric
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!