This question was originally posted on DCIM Support by Barry Patterson on 2019-07-17
InRow ACRC301S Chilled Water Flow has value of 0.0GPM as displayed from GUI. Verified by running SNMP MIB walk which has OID .188.8.131.52.4.1.3184.108.40.206.220.127.116.11.18.104.22.168 = INTEGER: 0. Possible bug with Chilled Water Flow sensor?
This answer was originally posted on DCIM Support by Balaraman Jagadeesan on 2019-07-18
Can you navigate to the below menu options on the unit display and confirm if you are read the Chilled Water Flow?
Main > Status > Detailed Status > Chilled Water Flow
If you see abnormal value over on the unit's display also, then I suggest you to contact your regional Schneider Electric's technical support as this may require certified cooling FSR to inspect this sensor in my opinion.
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!