This question was originally posted on DCIM Support by Ramu Manoharan on 2019-12-16
I m keep getting the error A-Link Bus power - value alert - overloaded, this error coming every 3 mints and goes normal and again coming, can you any one help me on this what exactly causing this and how to fix. I'm having netbotz rack monitor 570 (netbotz91190F) DCE device.
Thanks in advance.
This answer was originally posted on DCIM Support by Valentin Kozlov on 2019-12-16
This error indicates that A-Link bus is overloaded. May be you have many sensor pods connected to Netbotz. If so, you need to add external power supply in the middle of the chain.
If there are no external devices connected to A-Link port, it indicates that your Netbotz is broken.
This comment was originally posted on DCIM Support by Ramu Manoharan on 2019-12-16
Thanks for your reply...
this is an existing running environment, this error/issue started just 2 days before and there is no sensors added to the netbotz (recently or before the issue raises), kindly help.
This answer was originally posted on DCIM Support by GavOB on 2019-12-17
Is there any sensor pods attached to the Netbotz at all? If so can you kindly remove?
If not and your device is under warranty can you contact local support as there maybe be a hardware problem.
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!