Connecting to an ES that is on another machine through WorkStation and trying to force a BACnet input or output point located on a b3, connected to an AS-P, causes WorkStation to freeze. The only way to get out of freeze is by ending the system task in Windows.
EcoStruxure Building Operation
- Building Operation Enterprise Server v2.0.2.x
- Building Operation Automation Server v2.0.2.x
- Building Operation Workstation v2.0.2.x
- Continuum b3xxx Controller any version
EBO v2.0.2.x has communication issues when connecting to an ES that is not on the machine you have WorkStation on.
Upgrading to 18.104.22.168 or later will resolve this