In Building Operation Device Administrator the Name of the server there is a question mark (1) and the State of an AS-P is saying "SSL certificate validation failed!" (2).
EcoStruxure Building Operation
- Building Operation Automation Server Premium (AS-P)
- Building Operation Automation Server Bundled (AS-B)
- Building Operation Automation Server (AS)
The Automation Server has been added to Device Administrator with EBO server protocol HTTPS, but no SSL certificate has been generated and transferred to the server.
Follow the steps outlined in WebHelp section Device Administrator Certificate Workflow. When the certificate has been generated and transferred successfully to the Automation Server the correct server name will be displayed and the state will say Ready.