Changing the name of a folder under which there is an active alarm, causes an incorrect "Source" path in the alarm message
EcoStruxure Building Operation
Building Operation Workstation version 1.8 or earlier
If a folder name is changed it will be correctly updated, but if an active alarm is located in its sub-folders , then the alarm source path will not be updated.
Initial alarm before the folder name is changed, notice the source ...... FF IV/Trendloggar ......
The alarm after the folder name has been changed FF IV TEST, the / between FF IV TEST and Trendloggar is missing.
If the alarm has not been acknowledged, and clears a second entry for the alarm is displayed in the alarm view.
This is fixed in SBO/EBO 1.9 and later versions.
For versions 1.8 or earlier:
Before updating a EcoStuxure Building Operation(EBO) folder name, check to see if there are any active alarms with a source path that use this folder. If there are, try to clear these alarms.
If a EBO folder name has been changed and there are alarms in the alarm view which cannot be cleared, then use the "Recheck" command to clear them.