AS-P that has infinet devices connected to it, crashes during the Spring time-change of daylight savings.
EcoStruxure Building Operation
- Building Operation Automation Server
- Andover Continuum, infinet devices
Infinet schedules are sent down to the controller on a weekly basis. Having changed from default to be on Sunday between the time of 2:00 AM and 2:59 AM causes issues during daylight savings time "spring forward" due to that hour time span not existing. This causes the AS-P to crash.
If you have schedules being download differently from the default time interval, ensure that they are not being done on Sundays, between the time of 2:00 AM and 2:59 AM. If they are, update them forward or back an hour to avoid further issues.