AS-P controller fails to upgrade
EcoStruxure Building Operation
- Building Operation Workstation
- Building Operation Automation Server
- The upgrade still fails even after the DFU with a new database.
- Other AS-Ps on site were upgraded successfully.
- It may be required to DFU the AS-P more than once before the upgrade succeeds.
- NOTE: The DFU then upgrade process should not be performed more than 5 times. If after 5 times it still fails, the AS-P needs to be replaced.