This question was originally posted by Mihail on APC forums on 1/18/2017
What we know:
SymmetraPX (2) 100kW,
Dry contact interface AP 9613 set for configuration 2, only contact 6.
Issue : customer receives alarms for the regular UPS self test, when he should have gotten alarms only if there is a failure, like Self-Test failed.
Is this behaviour normal?
Have a question? Please contact us with details, and we will respond.
Look through existing questions to find popular answers.
Want to know more about Exchange and its possibilities?
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!
Register today for FREE
Already have an account?Log in