You can subscribe to this forum after you log in or create your free account..
Create your free account or log in to subscribe to the forum - and gain access to more than 10,000+ support articles along with insights from experts and peers.
Already have an account? Login
This was originally posted on APC forums on 11/6/2017
We have an APC UPS connected to a server and the UPS is being monitored by PCNS software.
We continually see messages in the log file …Site Wiring Fault.
It occurs at different times for different durations but is constant.
We also see the UPS kick onto the batteries for a few seconds than back to standard power.
This has been going on since the unit was installed earlier this year.
I marked down a few days’ worth of the time the events occurred last week.
An electrician connected a FLUKE meter to the power strip that connects to the UPS from the wall unit to record if there are any spikes.
He produced a report for last week and it does not show any abnormal power readings as compared to what PCNS is reporting.
Is there a specific setting or settings the FLUKE meter should be set to so that the issue can traced to why the APC keeps reporting the site wiring fault error and jumps to batter every so often?
Have a question? Please contact us with details, and we will respond.
Look through existing questions to find popular answers.
Want to know more about Exchange and its possibilities?
Register today for FREE
Already have an account?Login