You can subscribe to this forum after you log in or create your free account..
Create your free account or log in to subscribe to the forum - and gain access to more than 10,000+ support articles along with insights from experts and peers.
Already have an account? Login
This was originally posted on APC forums on 8/1/2007
Is anyone else having trouble with the ACSC100 standalone cooling unit condensate pumps not being able to keep up with removing the condensate water?
We have been having this problem for some time now and the units will SHUT DOWN. Fortunately, we have the building system HVAC as a backup in our small data center.
Since we have had this problem, even in the winter when humidity is typically low (Michigan), and we have seen this with both units, I suspect that there may be an issue with the pump itself.
Are we the only ones encountering this problem?
Have a question? Please contact us with details, and we will respond.
Look through existing questions to find popular answers.
Want to know more about Exchange and its possibilities?
Register today for FREE
Already have an account?Login