You can subscribe to this forum after you log in or create your free account..
Create your free account or log in to subscribe to the forum - and gain access to more than 10,000+ support articles along with insights from experts and peers.
Already have an account? Login
This was originally posted on APC forums on 7/11/2013
Recently I bought a rack automatic transfer switch ATS 7724. We have connected both UPS to both inputs: A and B.
I have only voltage in the outputs of the BANK 1 16A, but not the BANK 2.
Could someone help me?
Thank you very much.
This reply was originally posted by Angela on APC forums on 7/11/2013
First thing to do is check the status of the breaker for Bank 2.
Please review this document below and try full tripping the breaker and resetting it. Or let us know if the breaker is damaged.
See Answer In Context
Have a question? Please contact us with details, and we will respond.
Look through existing questions to find popular answers.
Want to know more about Exchange and its possibilities?
Register today for FREE
Already have an account?Login