topic Re: ION7650 in Metering & Power Quality
https://community.exchange.se.com/t5/Metering-Power-Quality/ION7650/m-p/161245#M3364
<P>I'm looking at the (default) ION7650v410 with 7650_FAC-PQ_V4.1.0.0.1 framework</P><P>assuming: 4W-WYE volts mode</P><P><STRONG>Displacement PF</STRONG>: My recomendation is to use the fundamental phase angles from the existing HME modules #1 through #6 (3s gapless 4-30 harmonic analysis). In order to compute the 3phase TOTAL displacement PF, you need to also compute the total fundamental powers.</P><P>The best implementation I can come up with on the spot uses three new ART modules.</P><P> </P><TABLE><TBODY><TR><TD> </TD><TD> </TD><TD> </TD><TD>ART40</TD><TD> </TD></TR><TR><TD>Input</TD><TD>Name</TD><TD>Label</TD><TD>Setup Formula</TD><TD>Output Label</TD></TR><TR><TD>1</TD><TD>HME2 Magnitude 1</TD><TD>V2 H1 Mag 3s</TD><TD>(S2-S4)*PI/180</TD><TD> </TD></TR><TR><TD>2</TD><TD>HME2 Phase 1</TD><TD>V2 H1 Ang 3s</TD><TD>S1*S3*cos(R1)/1000</TD><TD>fund kW2</TD></TR><TR><TD>3</TD><TD>HME5 Magnitude 1</TD><TD>I2 H1 Mag 3s</TD><TD>S1*S3*sin(R1)/1000</TD><TD>fund kVAR2</TD></TR><TR><TD>4</TD><TD>HME5 Phase 1</TD><TD>I2 H1 Ang 3s</TD><TD>S1*S3/1000</TD><TD>fund kVA2</TD></TR><TR><TD>5</TD><TD>HME3 Magnitude 1</TD><TD>V3 H1 Mag 3s</TD><TD>(S6-S8)*PI/180</TD><TD> </TD></TR><TR><TD>6</TD><TD>HME3 Phase 1</TD><TD>V3 H1 Ang 3s</TD><TD>S5*S7*cos(R5)/1000</TD><TD>fund kW3</TD></TR><TR><TD>7</TD><TD>HME6 Magnitude 1</TD><TD>I3 H1 Mag 3s</TD><TD>S5*S7*sin(R5)/1000</TD><TD>fund kVAR3</TD></TR><TR><TD>8</TD><TD>HME6 Phase 1</TD><TD>I3 H1 Ang 3s</TD><TD>S5*S7/1000</TD><TD>fund kVA3</TD></TR><TR><TD> </TD><TD> </TD><TD> </TD><TD> </TD><TD> </TD></TR><TR><TD> </TD><TD> </TD><TD> </TD><TD>ART41</TD><TD> </TD></TR><TR><TD>Input</TD><TD>Name</TD><TD>Label</TD><TD>Setup Formula</TD><TD>Output Label</TD></TR><TR><TD>1</TD><TD>HME1 Magnitude 1</TD><TD>V1 H1 Mag 3s</TD><TD>(S2-S4)*PI/180</TD><TD> </TD></TR><TR><TD>2</TD><TD>HME1 Phase 1</TD><TD>V1 H1 Ang 3s</TD><TD>S1*S3*cos(R1)/1000</TD><TD>fund kW1</TD></TR><TR><TD>3</TD><TD>HME4 Magnitude 1</TD><TD>I1 H1 Mag 3s</TD><TD>S1*S3*sin(R1)/1000</TD><TD>fund kVAR1</TD></TR><TR><TD>4</TD><TD>HME4 Phase 1</TD><TD>I1 H1 Ang 3s</TD><TD>S1*S3</TD><TD>fund kVA1</TD></TR><TR><TD>5</TD><TD>ART40 Result2</TD><TD>fund kW2</TD><TD> </TD><TD> </TD></TR><TR><TD>6</TD><TD>ART40 Result3</TD><TD>fund kVAR2</TD><TD>R2+S5+S7</TD><TD>fund kWtot</TD></TR><TR><TD>7</TD><TD>ART40 Result6</TD><TD>fund kW3</TD><TD>R3+S6+S8</TD><TD>fund kVARtot</TD></TR><TR><TD>8</TD><TD>ART40 Result7</TD><TD>fund kVAR3</TD><TD>sqrt(R6*R6+R7*R7)</TD><TD>fund kVAtot</TD></TR><TR><TD> </TD><TD> </TD><TD> </TD><TD> </TD><TD> </TD></TR><TR><TD> </TD><TD> </TD><TD> </TD><TD>ART42</TD><TD> </TD></TR><TR><TD>Input</TD><TD>Name</TD><TD>Label</TD><TD>Setup Formula</TD><TD>Output Label</TD></TR><TR><TD>1</TD><TD>IEEE PF Sign Convention</TD><TD>sqrt(S3*S3+S4*S4)</TD><TD> </TD></TR><TR><TD>2</TD><TD>ART41 Result6</TD><TD>fund kWtot</TD><TD>sqrt(S5*S5+S6*S6)</TD><TD> </TD></TR><TR><TD>3</TD><TD>ART41 Result2</TD><TD>fund kW1</TD><TD>sqrt(S7*S7+S8*S8)</TD><TD> </TD></TR><TR><TD>4</TD><TD>ART41 Result3</TD><TD>fund kVAR1</TD><TD>R1+R2+R3</TD><TD> </TD></TR><TR><TD>5</TD><TD>ART40 Result2</TD><TD>fund kW2</TD><TD>100*If(S1=0,1,If(S4>0,-1,1))*S3/R1</TD><TD>%DPF_1</TD></TR><TR><TD>6</TD><TD>ART40 Result3</TD><TD>fund kVAR2</TD><TD>100*If(S1=0,1,If(S6>0,-1,1))*S5/R2</TD><TD>%DPF_2</TD></TR><TR><TD>7</TD><TD>ART40 Result6</TD><TD>fund kW3</TD><TD>100*If(S1=0,1,If(S8>0,-1,1))*S7/R3</TD><TD>%DPF_3</TD></TR><TR><TD>8</TD><TD>ART40 Result7</TD><TD>fund kVAR3</TD><TD>100*If(S1=0,1,If(S4+S6+S8>0,-1,1))*S2/R4</TD><TD>%DPF_tot</TD></TR></TBODY></TABLE>Tue, 05 Mar 2019 00:04:56 GMTDanL2019-03-05T00:04:56ZION7650
https://community.exchange.se.com/t5/Metering-Power-Quality/ION7650/m-p/157600#M3316
<P>Hello everybody,</P><P> </P><P>I'm developing a multisite PME with ION7650, the customer is asking me a series of parameters but I haven't found them among the native measurements of the meter or in the standard graphic in PME.</P><P> </P><P>The parameters are:</P><P>- Displacement power factor (I haven't found it)</P><P>- Average PF (I haven't found it)</P><P>- Working time of the meter (I haven't found it)</P><P> </P><P> </P><P>I would like to know if I have to develop frameworks in designer to have these measurement or if any of them is already present natively in the meter.</P><P> </P><P>In addition, I saw:</P><P>- Crest factor of I and V : I saw they are available, but they're not present in the standard graphic</P><P>- Harmonics until the 63rd: I saw that in the standard graphic harmonics are shown up to the 15th, I need to see more.</P><P> </P><P>Should I modify the standard graphics or is there any quicker way to have these parameters displayed?</P><P> </P><P>Thanks in advance to whoever's gonna help me!</P>Thu, 20 Dec 2018 16:33:57 GMThttps://community.exchange.se.com/t5/Metering-Power-Quality/ION7650/m-p/157600#M3316sesa261168_brid2018-12-20T16:33:57ZRe: ION7650
https://community.exchange.se.com/t5/Metering-Power-Quality/ION7650/m-p/160566#M3336
<P>- Displacement power factor</P><P>Not calculated on the meter by default I believe, could you possibly calculate this from the phase angle of Current Versis phase angle of the voltage?</P><P> </P><P>- Average PF</P><P>Pf lag and PF Lead Mean from sliding demand window modules.</P><P> </P><P>- Working time of the meter</P><P>Not sure about this, possibly connect a counter module to clock module new day/hour</P>Wed, 20 Feb 2019 23:37:36 GMThttps://community.exchange.se.com/t5/Metering-Power-Quality/ION7650/m-p/160566#M3336Charles_Murison2019-02-20T23:37:36ZRe: ION7650
https://community.exchange.se.com/t5/Metering-Power-Quality/ION7650/m-p/161235#M3362
<P><LI-USER uid="27056"></LI-USER> </P>Mon, 04 Mar 2019 22:02:57 GMThttps://community.exchange.se.com/t5/Metering-Power-Quality/ION7650/m-p/161235#M3362Tom_Stevenson2019-03-04T22:02:57ZRe: ION7650
https://community.exchange.se.com/t5/Metering-Power-Quality/ION7650/m-p/161245#M3364
<P>I'm looking at the (default) ION7650v410 with 7650_FAC-PQ_V4.1.0.0.1 framework</P><P>assuming: 4W-WYE volts mode</P><P><STRONG>Displacement PF</STRONG>: My recomendation is to use the fundamental phase angles from the existing HME modules #1 through #6 (3s gapless 4-30 harmonic analysis). In order to compute the 3phase TOTAL displacement PF, you need to also compute the total fundamental powers.</P><P>The best implementation I can come up with on the spot uses three new ART modules.</P><P> </P><TABLE><TBODY><TR><TD> </TD><TD> </TD><TD> </TD><TD>ART40</TD><TD> </TD></TR><TR><TD>Input</TD><TD>Name</TD><TD>Label</TD><TD>Setup Formula</TD><TD>Output Label</TD></TR><TR><TD>1</TD><TD>HME2 Magnitude 1</TD><TD>V2 H1 Mag 3s</TD><TD>(S2-S4)*PI/180</TD><TD> </TD></TR><TR><TD>2</TD><TD>HME2 Phase 1</TD><TD>V2 H1 Ang 3s</TD><TD>S1*S3*cos(R1)/1000</TD><TD>fund kW2</TD></TR><TR><TD>3</TD><TD>HME5 Magnitude 1</TD><TD>I2 H1 Mag 3s</TD><TD>S1*S3*sin(R1)/1000</TD><TD>fund kVAR2</TD></TR><TR><TD>4</TD><TD>HME5 Phase 1</TD><TD>I2 H1 Ang 3s</TD><TD>S1*S3/1000</TD><TD>fund kVA2</TD></TR><TR><TD>5</TD><TD>HME3 Magnitude 1</TD><TD>V3 H1 Mag 3s</TD><TD>(S6-S8)*PI/180</TD><TD> </TD></TR><TR><TD>6</TD><TD>HME3 Phase 1</TD><TD>V3 H1 Ang 3s</TD><TD>S5*S7*cos(R5)/1000</TD><TD>fund kW3</TD></TR><TR><TD>7</TD><TD>HME6 Magnitude 1</TD><TD>I3 H1 Mag 3s</TD><TD>S5*S7*sin(R5)/1000</TD><TD>fund kVAR3</TD></TR><TR><TD>8</TD><TD>HME6 Phase 1</TD><TD>I3 H1 Ang 3s</TD><TD>S5*S7/1000</TD><TD>fund kVA3</TD></TR><TR><TD> </TD><TD> </TD><TD> </TD><TD> </TD><TD> </TD></TR><TR><TD> </TD><TD> </TD><TD> </TD><TD>ART41</TD><TD> </TD></TR><TR><TD>Input</TD><TD>Name</TD><TD>Label</TD><TD>Setup Formula</TD><TD>Output Label</TD></TR><TR><TD>1</TD><TD>HME1 Magnitude 1</TD><TD>V1 H1 Mag 3s</TD><TD>(S2-S4)*PI/180</TD><TD> </TD></TR><TR><TD>2</TD><TD>HME1 Phase 1</TD><TD>V1 H1 Ang 3s</TD><TD>S1*S3*cos(R1)/1000</TD><TD>fund kW1</TD></TR><TR><TD>3</TD><TD>HME4 Magnitude 1</TD><TD>I1 H1 Mag 3s</TD><TD>S1*S3*sin(R1)/1000</TD><TD>fund kVAR1</TD></TR><TR><TD>4</TD><TD>HME4 Phase 1</TD><TD>I1 H1 Ang 3s</TD><TD>S1*S3</TD><TD>fund kVA1</TD></TR><TR><TD>5</TD><TD>ART40 Result2</TD><TD>fund kW2</TD><TD> </TD><TD> </TD></TR><TR><TD>6</TD><TD>ART40 Result3</TD><TD>fund kVAR2</TD><TD>R2+S5+S7</TD><TD>fund kWtot</TD></TR><TR><TD>7</TD><TD>ART40 Result6</TD><TD>fund kW3</TD><TD>R3+S6+S8</TD><TD>fund kVARtot</TD></TR><TR><TD>8</TD><TD>ART40 Result7</TD><TD>fund kVAR3</TD><TD>sqrt(R6*R6+R7*R7)</TD><TD>fund kVAtot</TD></TR><TR><TD> </TD><TD> </TD><TD> </TD><TD> </TD><TD> </TD></TR><TR><TD> </TD><TD> </TD><TD> </TD><TD>ART42</TD><TD> </TD></TR><TR><TD>Input</TD><TD>Name</TD><TD>Label</TD><TD>Setup Formula</TD><TD>Output Label</TD></TR><TR><TD>1</TD><TD>IEEE PF Sign Convention</TD><TD>sqrt(S3*S3+S4*S4)</TD><TD> </TD></TR><TR><TD>2</TD><TD>ART41 Result6</TD><TD>fund kWtot</TD><TD>sqrt(S5*S5+S6*S6)</TD><TD> </TD></TR><TR><TD>3</TD><TD>ART41 Result2</TD><TD>fund kW1</TD><TD>sqrt(S7*S7+S8*S8)</TD><TD> </TD></TR><TR><TD>4</TD><TD>ART41 Result3</TD><TD>fund kVAR1</TD><TD>R1+R2+R3</TD><TD> </TD></TR><TR><TD>5</TD><TD>ART40 Result2</TD><TD>fund kW2</TD><TD>100*If(S1=0,1,If(S4>0,-1,1))*S3/R1</TD><TD>%DPF_1</TD></TR><TR><TD>6</TD><TD>ART40 Result3</TD><TD>fund kVAR2</TD><TD>100*If(S1=0,1,If(S6>0,-1,1))*S5/R2</TD><TD>%DPF_2</TD></TR><TR><TD>7</TD><TD>ART40 Result6</TD><TD>fund kW3</TD><TD>100*If(S1=0,1,If(S8>0,-1,1))*S7/R3</TD><TD>%DPF_3</TD></TR><TR><TD>8</TD><TD>ART40 Result7</TD><TD>fund kVAR3</TD><TD>100*If(S1=0,1,If(S4+S6+S8>0,-1,1))*S2/R4</TD><TD>%DPF_tot</TD></TR></TBODY></TABLE>Tue, 05 Mar 2019 00:04:56 GMThttps://community.exchange.se.com/t5/Metering-Power-Quality/ION7650/m-p/161245#M3364DanL2019-03-05T00:04:56ZRe: ION7650
https://community.exchange.se.com/t5/Metering-Power-Quality/ION7650/m-p/161247#M3365
<P><STRONG>For Average PF</STRONG>: do <U>NOT</U> simply use a sliding window demand module to compute a time averaging of the power factor ratio. This does not make sense mathematically to perform an un-weighted average... instead you must divide the time averaged real power [kW] by the time averaged average apparent power [kVA] (and multiply by your preffered sign convention).</P>Tue, 05 Mar 2019 00:08:21 GMThttps://community.exchange.se.com/t5/Metering-Power-Quality/ION7650/m-p/161247#M3365DanL2019-03-05T00:08:21ZRe: ION7650
https://community.exchange.se.com/t5/Metering-Power-Quality/ION7650/m-p/161250#M3366
<P>I do not have the exact framework, but in older ION7650 meters (before V350), there was the "Power Availability Framework".</P><P>Looking at the ION Device Template Reference, it may be possible to re-build this. I believe this framework was taken out becuase of processing space so it may need to be trimmed down or possibly other features removed.</P><P><A href="https://www.schneider-electric.com/en/download/document/ION_Device_Template_Reference/" target="_blank">https://www.schneider-electric.com/en/download/document/ION_Device_Template_Reference/</A></P>Tue, 05 Mar 2019 01:09:56 GMThttps://community.exchange.se.com/t5/Metering-Power-Quality/ION7650/m-p/161250#M3366Charles_Murison2019-03-05T01:09:56ZRe: ION7650
https://community.exchange.se.com/t5/Metering-Power-Quality/ION7650/m-p/161486#M3369
<P><LI-USER uid="20221"></LI-USER> - does this give you what you need?</P><P><BR />Thanks</P><P><BR />Tom</P>Thu, 07 Mar 2019 21:00:56 GMThttps://community.exchange.se.com/t5/Metering-Power-Quality/ION7650/m-p/161486#M3369Tom_Stevenson2019-03-07T21:00:56Z